PRODUCT SPECIFICATIONS &
Max. Voltage: 300V
Wire Type: Copper/Aluminum
Temperature Rating: 105°C
Flammability Rating: V-2
Do not reuse
One conductor only per port
2 Port Aluminum to Copper Lug (AL-CU)
Catalog # Selling Unit
95015 Bag of 10
95025 Bag of 25
95035 Box of 100
95045 Box of 1000
95085 Box of 2500
2 Port AlumiConn
Aluminum to Copper Lug
UL 486C Listed to meet U.S.
and Canadian specifications
as a Pressure Screw Type
UL LISTED INSTALLATION INSTRUCTIONS
IMPORTANT: Turn off power before installing or removing connector.
Product to be used in accordance with local and national codes.
1. Strip conductors 5/16”.
2. Insert conductor into wire port, fully seating conductor into port.
3. Tighten set screws to the torque indicated below, based on conductor size and material as
indicated. 10 in-lb #12 solid aluminum
15 in-lb #10 solid aluminum
15 in-lb all solid and stranded copper conductors
Do not over torque.
4. Once all conductors are installed, close lid taking care to verify latch is securely fastened.
Not following recommended torque instructions can result in failure.
To be sold only with installation instructions.
300V WIRE SIZES
#12 - #10 Solid Aluminum
#18 - #10 Solid and Stranded Copper
Made in U.S.A.
Consumer Products Safety Commission (CPSC)
as a long-term repair
method for aluminum wiring
SUPERIOR QUALITY THROUGH...
• Secure, mechanical connection of conductors
• Provides more safety
U.S. Pat. 9,172,167 and additional Patents Pending apply.
All other trademarks, U.S. and Foreign Patents apply. All Rights Reserved.