PRODUCT SPECIFICATIONS &
Max. Voltage: 300V
Wire Type: Copper/Aluminum
Temperature Rating: 105°C
Flammability Rating: V-2
Do not reuse
One conductor only per port
3 Port Aluminum to Copper Lug (AL-CU)
Catalog # Selling Unit
95104 Card of 2
95110 Card of 10
95125 Bag of 25
95135 Box of 100
95145 Box of 1000
95185 Box of 2500
3 Port AlumiConn
Aluminum to Copper Lug
UL 486C Listed to meet U.S.
and Canadian specifications
as a Pressure Screw Type
SUPERIOR QUALITY THROUGH...
• Secure, mechanical connection of conductors
• Provides more safety
UL LISTED INSTALLATION INSTRUCTIONS
IMPORTANT: Turn off power before installing or removing connector.
Product to be used in accordance with local and national codes.
1. Strip conductors 5/16”.
2. Insert conductor into wire port, fully seating conductor into port.
3. Tighten set screws to the torque indicated below, based on conductor size and material as
indicated. 10 in-lb #12 solid aluminum
15 in-lb #10 solid aluminum
15 in-lb all solid and stranded copper conductors
Do not over torque.
4. Once all conductors are installed, close lid taking care to verify latch is securely fastened.
Not following recommended torque instructions can result in failure.
To be sold only with installation instructions.
300V WIRE SIZES
#12 - #10 Solid Aluminum
#18 - #10 Solid and Stranded Copper
Consumer Products Safety Commission (CPSC)
as a long-term repair
method for aluminum wiring
Made in U.S.A.
U.S. Pat. 9,172,167 and additional Patents Pending apply.
All other trademarks, U.S. and Foreign Patents apply. All Rights Reserved.