SOPHIA MULTI-ZONE INVERTER WIRED CONTROL FOR AIR CONDITIONER INSTALLATION MANUAL IMPORTANT NOTE: Read this manual carefully before installing or operating your wired remote control. Make sure to save this manual for future reference.
Table of Contents Wall-Mounted Remote Control Wiring...............................1 Wall-Mounted Remote Control Installation ........................
Wall-Mounted Remote Control Wiring WARNING The wiring should adapt to the wire control current. Otherwise, electric leakage or overheating may occur and result in fire. • The specified cables must be used in the wiring. No external force should be applied to the terminal. Otherwise, the wire may be damaged and heating may occur and result in fire. • CAUTION The shielded wire must be grounded. The connecting cable shouldn't be longer than 20 m (65.5 ft).
An overview of the wall-mounted remote control wire outlet Top side wire outlet Right side wire outlet Left side wire outlet Bottom side wire outlet Fig. 1 1. Wiring diagram Refer to the following diagram to wire the wall-mounted remote control to the indoor unit. Wired joint, 5p Wired control Infrared pipe +5V 5-Core shield cable RUN GND Indoor unit switchboard Fig.
2. Installation Diagram Connect the wire from the display panel of the indoor unit to a connecting cable. Then connect the other side of the connecting cable to the remote control. The connective wires group 5-core wire Front grille Fig. 3 NOTE: Be sure to reserve a length of the connecting wire for periodic maintenance.
NOTE: DO NOT allow water to enter the remote control. Use the trap and putty to seal the wires. Putty Trap Putty Putty Trap Trap Fig. 4 a. For exposed mounting, cut holes on four of the sides according to Fig. 5. b. For shielded wiring, please refer to Fig. 6.
Cut three holes for wire outlet Cut one hole for wire outlet Fig. 5 Embedded switch box wiring Wiring hole Wiring through the wall Wall hole and wiring hole Diameter of wall hole: Φ 2cm Fig.
Wall-Mounted Remote Control Installation WARNING DO NOT operate the unit with wet hands, as this could lead to electrical shock. Remote Control Dimensions 120 mm (4.7 in) 21 mm (0.8 in) 13.1 mm (0.5 in) 19.5 m m 19.5 mm (0.7 in) 51.1 mm (2 in) 120 mm (4.7 in) 85.5 mm (3.3 in) 50 mm (1.9 in) Fig.
Preparation before Installation 1. Be sure you have the following parts: Table 1 No Name Quantity Remarks 1 Remote control 1 2 Screws 3 3 Anchors 3 For mounting on the wall 4 Screws 2 M4x25 (for mounting on switch box) 5 Plastic screw bars 2 For fixing on the switch box 6 The connective wires group 1 Optional M4x20 (for mounting on the wall) 2. Prepare the following tools: Table 2 No Name Quantity 1 Switch box 1 2 Wiring tube (insulating sleeve and tightening screw) 1 3.
Installation Method 1. Remove the top panel of the remote control: Insert a screwdriver into the two slots at the bottom of the remote control to pop off the top panel. Slots Fig. 8 NOTE: The printed circuit board (PCB) is mounted in the upper part of the remote control. Be careful not to damage the board with the screwdriver. 2. Mount the back plate of the remote control: a. For exposed mounting, fasten the back plate to the wall with 3 screws (M4×20) and anchors.
Back plate Screws (M4×20) Fig. 9 b. For flush mounting, fasten the back plate to the switch box with 2 screws (M4×25) and fasten the back plate to the wall with 1 screw (M4×20). Switch box Back plate Screw (M4×20) Screws (M4×25) Fig. 10 NOTE: Place the unit on a flat surface. Be careful not to distort the back plate of the remote control by overtightening the screws.
3. Set the time and date: The remote control has a small, built-in battery that allows the time and date to be set. This allows the remote control to keep time even during a power outage. When the unit displays an incorrect time and date, the batteries need to be replaced. 4. Reattach the top panel of the remote control: Fig. 11 CAUTION DO NOT clamp the wires when reattaching the top panel.
QSXI-005AEN The design and specifications are subject to change without prior notice for product improvement. Consult with the sales agency or manufacturer for details.