High Power Lighting Module INSTALLATION AND OPERATING INSTRUCTIONS For Models: XP4LS XP1LS 10012 North Dale Mabry, Ste. 115 Tampa, FL 33618 Tel: (800) TECH-003 Fax: (813) 265-1011 Email: firstname.lastname@example.org Web: www.X10PRO.
Congratulations! You have just purchased the best quality powerline carrier lighting module available. X-10 PRO's Lighting Module is a high quality, X-10 compatible product that is a low cost alternative to hard-wired lighting systems. This booklet covers all X-10 PRO models XP4LS and XP1LS. CAUTION!! READ AND UNDERSTAND THESE INSTRUCTIONS BEFORE INSTALLING DEVICE. This device is intended for installation in accordance with the National Electric Code and local regulations.
WIRING CONFIGURATION The Lighting Module is wired directly to the lighting circuit and can be controlled by one or more Remote switches producing three, four, or five-way circuits. Multiple-way circuits make it possible for a group of switches to control the same set of lights. This section will illustrate how to hook-up the connections.
PRE-WIRING for X-10 PRO's Lighting Modules The following is a guide to a “home-run” type wiring configuration that ensures a versatile and reliable system. This configuration costs slightly more in materials and labor to run the 14 gage home-runs for each load and control point. This expense, however, is more than offset by the increase in system reliability having all associated lighting and control points electrically “close” or in the same vicinity.
Whole House Wiring The three important things to remember when wiring for controlled lighting are: 1. Wire fixture (load) circuits and control (transmitter/switch) circuits separately back to a common location ("home-run" method). 2. Use a deep four gang box or boxes as the junction point for loads, controls and power.
REMOTE SWITCH OPERATION Turning the Lighting Circuit On Tap the Rocker Top once. Turn On to Full Bright Tap the Rocker Top twice. Brightening the Lighting Circuit Turning the Lighting Circuit Off Hold Top down until lighting level is achieved. Tap the Rocker Bottom once.
To Enter any Mode: 1) Press and hold down the PROGRAM button and release it when the LED starts blinking green. You are now in Mode 1 (Setting New Primary Address). 2) Tap the PROGRAM button once. The LED is blinking red. You are in Mode 2 (Setting New Scene Addresses). 3) Tap the PROGRAM button once. The LED is blinking orange. You are in Mode 3 (Setting Channel Enables). 4) Tap the PROGRAM button once. The LED is alternating green and red. You are in Mode 4 (Setting Ramp Rates).
Mode 2 Programming - Setting Scene Addresses 1) Enter Mode 2. See To Enter any Mode section. 2) Press Scene Number. A number between 1 and 16 representing scene of product. 3) Press All-Lights-On key. Product confirms Scene Number is entered. 4) Transmit X-10 address. Address will be the address of the scene number selected. 5) Press All-Lights-On key. The product stores new Scene Address into memory. 6) Press All-Lights-On key 3 times.
Mode 5 Programming - Setting Advanced Programming Options The Advanced Programming Options are given the following table. The sequence of programming is different for these options, so we will separate them as follows. Advanced Programming Options 1 through 7 1) Enter Mode 5. See To Enter any Mode section. 2) Press Advanced Programming Option number. A number between 1 and 7 as defined in the following table. 3) Press All-Lights-On key. Product confirms Option Number is entered.
Advanced Programming Option 9 1) Enter Mode 5. See To Enter any Mode section. 2) Press Advanced Programming Option 9. Press key "9" which is defined in the following table. 3) Press All-Lights-On key. Product confirms Option Number is entered. 4) Press the Receive Level. A number between 1 and 16 representing the voltage receive level of the product. The default is "4" (50mV). The "1" key is 5mV, "7" is 125mV, "11" is 225mV, "14" is 300mV, and "16" is 350mV. 5) Press All-Lights-On key.
Default Settings The default settings for the four channel modules (XP4LSs) are shown in the tables below. The single channel module (XP1LS) are the same except for the absence of channels 2, 3 and 4.
SPECIFICATIONS Model Number XP4LS XP1LS Operation Dimming (Triac) Dimming (Triac) Max Total Load 2000 W / 2000 VA 2000 W / 2000 VA Channels Four One Max Channel Load 1000 W 2000 W Standard Load Types Incandescent, Magnetic Low Voltage Incandescent, Magnetic Low Voltage Input Power 125 VAC 125 VAC Min Load 60 W 60 W Min Receive Level 5 mV 5 mV Max Noise Rejection 350 mV 350 mV Connections 16 AWG 16 AWG LED Indicator Yes Yes 3 3 Dimensions 11.0 X 5.0 X 1.63 in 11.0 X 5.